Read or Download BP Process Safety Series - Safe Furnace and Boiler Firing PDF
Best mechanical engineering books
Thermodynamic equipment of research have in recent times chanced on ever-growing extensions in assorted areas of contemporary tech nology. the article of the current publication is to use those the right way to the outline of fabrics of various actual homes. i'm hoping the e-book will illustrate the wide range and usability of thermodynamics which was once good defined by means of Albert Einstein: "A conception is the extra notable the better the simplicity of its premises is, the extra other forms of items it relates, and the extra prolonged is its zone of applicability.
This 3rd version of the spouse advisor of ASME Boiler & strain Vessel and Piping Codes has been up to date to the present (2007) Code variation. because the first version, a complete of a hundred and forty authors have contributed to this booklet, and during this version there are 107 participants of which fifty one are new authors.
This crucial new quantity offers historical past details, historic standpoint, and specialist statement at the ASME B31. three Code standards for method piping layout and building. It offers the main entire insurance of the Code that's to be had this present day and is choked with additional info necessary to these answerable for the layout and mechanical integrity of method piping.
Additional info for BP Process Safety Series - Safe Furnace and Boiler Firing
The valves’ safety system has to be overridden to do this. continued 26 SAFE FURNACE A N D BOILER FIRING rhere is a platform on top of the furnace (which is 25 metres high) to facilitate naintenance work and control activities. rhree workers were on the top of the furnace replacing the insulation after ninor maintenance when the start-up procedure was begun. lespite the procedure, the overridden safety system was not reactivated, eaving the valves open. When the gas supply was then opened, the nitrogen n the pipe was flushed out by natural gas, and gas flowed through the open nput valves into the furnace.
The explosion caused the radiant section enclosure of the fired heater to burst/breaking seam bolts, dislodging supports for the convection section overhead and knocking down a number of vertical tubes from their hangers. Fire erupted in the radiant section and continued to be fed with fuel from the ethylbenzenetower due to failed tubes. H continuea 46 SAFE FURNACE A N D BOILER FIRING More than 150 fire-fighters were involved in fighting the fire. Water cooling streams were strategically applied onto the support structure to guide the collapsing convection chamber, flue and stack into an open area on the plant site.
If the flame continues to burn in the mixing tube, the burner should be shut off and allowed to cool before relighting. Flashbacks cannot occur if (1) the gas-air mixture in the mixing tube is too rich to burn or (2) if the velocity of the mixture through the spider holes exceeds the velocity at which the flame will travel backwards in the mixture. Thus, 36 SAFE FURNACE AND BOILER FIRING flashbacks can be prevented by reducing primary air to produce a rich mixture in the mixing tube or by increasing the firing rate so that the velocity through the spider holes exceeds the backward velocity of the flame.